The working principle of the combined superheated steam trap source: Sansheng trap time: 2019-12-23 clicks:
Combined superheated steam trap:
The combined superheated steam trap has two isolated valve chambers, which are connected by two stainless steel pipes to the upper and lower valve chambers. It is a combination of float and inverted bucket traps. The valve structure is advanced and reasonable. Under the working condition of small load, the condensed water formed when the superheated steam disappears can be timely discharged, the leakage of the superheated steam can be effectively prevented, and the work quality is high. The maximum allowable temperature is 600 ℃, the valve body is all stainless steel, the valve seat is hard alloy steel, and the service life is long. It is a special steam trap for superheated steam. It has obtained two national patents and filled the domestic blank.
Free Float Steam Trap 3
When the condensed water enters the lower valve cavity, the float of the auxiliary valve rises with the liquid level, and the float closes the inlet pipe hole. The condensed water rises to the main valve cavity through the water inlet conduit, and the inverted bucket falls by its own weight, which drives the valve core to open the main valve and discharge the condensed water. When the level of the condensed water in the auxiliary valve cavity drops, the float drops with the liquid level and the auxiliary valve opens. The steam enters the inverted bucket in the upper main valve cavity from the steam inlet pipe. The inverted bucket generates upward buoyancy, and the inverted bucket drives the valve core to close the main valve. When the level of the condensate in the auxiliary valve cavity rises again, the next cycle starts again, and the drainage is intermittent.
Want to know more about traps, lever float ball traps, trap manufacturers, please continue to pay attention to the official website of Wuxi Sansheng Printing and Dyeing Machinery Co., Ltd. chikob.com